are specifi ed relative to the
main air connection at 12 oclock and should be listed
pilot, gas, and fl ame detector in that order.
practice dictates that neither the pilot nor the fl ame
supervision device be on the bottom of the burner.
ATP BURNER TILE INSTALLATION RECOMMENDATIONS FOR HARD REFRACTORY LINED FURNACES
Furnace opening should be ½" larger than dimension EE for -8 thru -14; ¾" larger than dimension EE for -16 thru -24.
Any tile length greater than GG × 1.2 should have a 30° angled fl are from the standard tile extension.
Two wraps of ½" soft fi berglass rope (Davlyn #100801 or equivalent) suitable for 1000 F service. North American can supply as part no. R540-0365.
Specify length when ordering.
Expansion joints must be provided in surrounding refractory to prevent pressure being exerted on cast or rammed burner tunnel section.
Burners are designed to be mounted no more than 15° from horizontal. Contact your North American Sales Engineer if your application requires a greater angle.
t © 2020 - F
es - All r
ved | Dims & Inst
all 4482 05/01
Fives North American Combustion, Inc.
4455 East 71st Street - Cleveland, OH 44105 - USA
T +1 800 626 3477 - F +1 216 373 4237